The review of these plans is to ensure the proper design and calculations are provided for compliance, with the above listed code, prior to the installation of the fire alarm and smoke detection system.
No. Fire Code Compliance Item
A-000 APPLICABLE CODES:
This code reference shall be placed on the cover sheet of your drawings "These plans were reviewed using NFPA 72; National Fire Code; 2013 Ed."
A-002 Provide floor plans to include room designations and room dimensions NFPA 72; Chap. 7; Sect 7.4.5; 2013 Ed.
A-003 Provide a sheet that identifies the matrix of operations for all systems and devices, with any design assumptions. NFPA 72; Chap. 7; Sect. 7.2.1(4); 2013 Ed.
A-004 Provide point to point wiring diagrams including end of line resistors. NFPA 72; Chap. 7; Sect. 7.4.8; 2013 Ed.
A-006 Provide appliance / device / equipment spec sheets. NFPA 72; Chap. 7; Sect. 7.2.1(5); 2013 Ed.
A-008 Provide a copy of low voltage license. NFPA 72; Chap. 10; sect. 10.5.2; 2013 Ed.
A-010 Is building equipped with an automatic sprinkler system? Authority Having Jurisdiction.
A-012 Provide mounting heights of pull stations (42-54 inches above finished floor). Georgia Accessibility Code; Chap. 3; Sect 308; 2010 Ed.
A-014 Provide mounting heights of strobes wall mount (80 inches above finished floor). Ceiling mounted strobe maximum of 30 feet above finished floor. NFPA 72; Chap. 18; Sect. 22.214.171.124, 126.96.36.199 and 188.8.131.52.6; 2013 Ed.
A-016 Provide automatic sprinkler riser details if more than (1) riser is installed. Authority Having Jurisdiction.
A-018 Provide symbols for devices used in fire alarm and identify candela size. NFPA 72; Chap. 7; Sect. 7.2.3; 2013 Ed.
A-020 Provide class of system. NFPA 72; Chap. 12; Sect. 12.3; 2013 Ed.
A-022 Provide secondary power supply. NFPA 72; Chap. 10; Sect. 10.6.7; 2013 Ed.
A-024 Provide plenum rated wire above ceiling. NFPA 72; Chap. 7; Sect 7.4.5 (12).
A-026 Provide Non-plenum rated wire. NFPA 72; Chap. 7; Sect. 7.4.5 (12).
A-028 Provide annunciator panel location in lobby / reception area or at a constantly attended location. NFPA 72; Chap. 10; Sect. 10.18.3; 2013 Ed.
A-030 Verify Fire Alarm control panel location. Make sure it is placed in a UL approved protected enclosure or placed in an environmentally protected area. Must meet the temperature ranges of 32 to 120 degrees Fahrenheit. NFPA 72; Chap. 10; Sect. 10.18.3.2; 2013 Ed.
A-032 Identify all Fire Alarm zones at annunciator. NFPA 72; Chap. 10; Sect. 10.18.4; 2013 Ed.
A-034 Hood system shall be wired to Fire Alarm. NFPA 17A; Chap. 5; Sect. 5.3.1.
A-036 Provide detector in Elevator lobby. NFPA 101; Chap. 9; Sect. 184.108.40.206.2; 2012 Ed.
A-038 Provide detector above Fire Alarm Control panel. NFPA 72; Chap. 10; Sect. 10.4.4.
A-040 Verify if HVAC duct detectors show trouble and shut unit down. NFPA 72; Chap. 17; Sect. 220.127.116.11.4(2); 2013 Ed.
A-042 Provide a smoke or heat detector for Automatic door release. NFPA 72; Chap. 17; Sect. 18.104.22.168; 2013 Ed.
A-044 Provide supervision for Dry pipe sprinkler systems. NFPA 72; Chap. 17; Sect 22.214.171.124.2; 2013 Ed.
A-046 Provide supervision for Control valves. NFPA 72; Chap. 17; Sect. 17.16.1; 2013 Ed.
A-048 Provide supervision for Pressure sources. NFPA 72; Chap. 17; Sect 126.96.36.199.1; 2013 Ed.
A-050 Provide supervision for Water level. NFPA 72; Chap. 17; Sect. 17.16.3; 2013 Ed.
A-052 Provide supervision for Water temperature. NFPA 72; Chap. 17; Sect 17.16.4; 2013 Ed.
A-054 Provide supervision for Fire pump. NFPA 72; Chap. 23; Sect. 188.8.131.52.2; 2013 Ed.
A-056 Provide supervision for automatic phone dialer for offsite monitoring. NFPA 72; Chap. 26; Sect. 184.108.40.206; 2013 Ed.
A-058 Provide voice evacuation in places of assembly with an occupant load of 300 persons or more. NFPA 101; Chap. 12; Sect 220.127.116.11.6; 2012 Ed.
A-060 Provide voice evacuation with alternate power supply. NFPA 101; Chap. 9; Sect. 18.104.22.168.2(2); 2012 Ed.
A-062 Verify if speakers override sound system. NFPA 101; Chap. 9; Sect. 22.214.171.124.2(3); 2012 Ed.
A-064 Provide voice evacuation with automatic operation. NFPA 101; Chap. 9; Sect. 126.96.36.199; 2012 Ed.
A-066 Provide voice evacuation with microphone and manual override. NFPA 101; Chap. 9; Sect. 188.8.131.52.2(4); 2012 Ed.
A-068 Provide a fire alarm and/or smoke detection system complying with the requirements of the occupancy chapter of the NFPA 101 Life Safety Code, 2012 Ed.
A-070 Provide mini horn in apartment dwelling units to achieve minimum db. Authority having Jurisdiction.